Introduction of welding stainless steel water tank:
Stainless steel water tank use imported sus304 stainless steel material,meet the national health inspection standards,no rust,
no green moss,no leakage,permanently maintain sanitation,steady and safe,useful life is 15 times more than concrete water tank,and can be used in cold water,water purification, hot water,chemicassolvents and so on.
Totally enclosed,there are inlet,outlet,overflow,sewage function,simple installation. You just need to put the tank on the roof,receive on conduit went,the maintenance is very convenient.
The sectional panel tank shall consist of 4′ x 4′ or 1 meter x 1 meter,1 meter x 0.5 meter
panel manufactured from 1.5mm to 4.0mm thickness according to requirement.
The sectional panels shall be pressed to double flanges at the angles of 45 degree and 90 degree to the face of the plate on four sides.
3. Reinforcement Method
All tanks are internally braced with angle stays to endure the rigidity of the tank when filled with the water. The Top panel is supported by top panel support, which shall be made of stainless steel grade 304 or 316 material according to requirement.
1. Bolt. nut & washers stainless steel 304 material.
2. Sealing material Non-toxic P.V.C foam tape shall be used in between the joints.
3. Covers The tank cover shall be constructed from 1.2mm to 3.0mm of thickness stainless steel 304 material according to the requirement.
4 Ladders and Level Indicator
Internal & external ladder shall be made of stainless steel grade 304 material.