Water reservoir tank installation and commissioning steps:
The foundation can be concrete beam, or I-beam. The top of the tank is equipped with ventilation air filter on the top, the size and quantity according to the size of the import size determined by the user or our device. Tanks are used inside the tank. The mouth flange are 1.0 MPa standard flange.
In the layout of the tank location, should refer to GB17051-1997 secondary water supply facilities health norms. Water tank specifications Technical parameters or orientation and the actual use of unsuitable, by the tank design staff in accordance with the actual needs of the identified.
Water reservoir tank installation instructions
A. Water tank foundation requirements The concrete foundation geometric size should be GB02S101 the relevant provisions of the development. Concrete foundation plane height difference <5 mm
B. Stainless steel water tank installation, construction and acceptance of professional welder on-site argon arc welding. Construction site has a standard power supply. Around the water tank ‰¥ 500 mm maintenance space. Appearance inspection without rust, no pollution: fill with water 2-3 H, no significant distortion box, no leakage of qualified weld.
C. The use of the tank, repair and maintenance piping, not to the piping inlet and outlet to exert excessive load. Do not apply the weight of the valve and the large diameter pipe directly to the water tank outlet. If necessary, set the pipe support: the expansion, contraction and vibration of the welded pipe must be equipped with telescopic flexible joint.
Stamping stainless steel welded steel tanks with stainless steel stamping out the ribs and welded with stainless steel welded the whole, simple structure, strength, and can create a larger capacity of the water tank. Because the box with stainless steel plate welding, completely cut off the sunlight, it will not breed algae. So that water is always kept clean.