What is tankless water system?
No water supply pressure canister Italy to understand what is no water pressure tank to start from the early tradition of tankless water system supply mode, the early rural collective water supply and some units, schools with the pressure pump to Water pump to a high water tower above, and then by the water tower to produce a high degree of static pressure to the water supply, a obvious feature is a very high water tank, then each household their own water when switching to high water tank stainless steel— In fact, is a form of water tank. No tank water supply is to cancel the water tank, directly with the pump and pressure tank mode to replace the high water tower, with the pressure switch to control the pump start and stop, the Akustan pressure tank buffer water hammer and extend the pump sleep.
Since the tankless water system pressure is higher than the pressure of the pre-filled gas, a portion of the working medium is introduced into the airbag (in the case of a diaphragm) into the tank until a new pressure is reached in the system Balance, when the system pressure increased, the system pressure again greater than the pressure of pre-filled gas, there will be part of the media into the capsule, the compression between the capsule and the gas tank, the gas compression pressure increased when the system with the system When the pressure is the same, the medium stops entering. On the contrary, when the system pressure drops, the medium pressure in the system is lower than the gas pressure between the capsule and the tank, the water inside the airbag will be added to the system by gas extrusion, Until the system working medium pressure and the pressure between the capsule and the tank gas pressure equal to the capsule of water outside the system is no longer supply to maintain the dynamic balance.
tankless water system role:
Is widely used in central air conditioning, boilers, water heaters, variable frequency, constant pressure water supply equipment, the buffer system pressure fluctuations, eliminating the role of water hammer to stabilize the unloading pressure in the system, a slight change, the automatic expansion of the balloon Shrinkage will have a certain buffer on the impact of changes in water pressure to ensure that the system of water pressure stability, the pump will not change due to frequent pressure to open.
Italy Acustan no tower water pressure tank in accordance with the following points to install, you can avoid some of the trouble caused by the installation is not, simple and effective.
1, the heating system is recommended to be installed in the system relative to the lowest point of water temperature, usually installed in the system backwater side, the storage tank of cold water into the water side. 24L and 24L below the pressure tank can be directly connected to the system because of its light weight pipe. To avoid the tank in the work of water and the weight of the system to produce a greater load on the pipeline, for more than 24L with its own three-legged bracket, metal hose can be connected to the system, buried screw fixation no tower water pressure tank feet, To ensure the smooth use of the process,
2, to be installed near the safety valve to avoid damage in the system when the pressure is abnormal pressure tank and other parts of the system;
3, in the heating and air conditioning closed circulation system, can not be installed in the water pump outlet, this may cause the pump cavitation.
4, in the heat system such as air conditioning, boilers, heat pumps and other general installed in the system backwater.